|Product Name:||Tank Series Two Luminaires Assembly LED Explosion Proof Flood Light Fixtures||Operating Voltage:||100-277 VAC,347-480 VAC,141-391VDC,491-679 VDC|
|Power:||160W,200W,240W||Available Cable Outer Diameter:||φ7-φ20(mm)|
|Cable Entries:||2XM20*1.5 (NPT 3/4”, M25*1.5 Are Optional)||IP Code:||IP 66|
|Enclosure Material:||Aluminium||Protective Cover:||Tempered Glass,Stand 7J Impact|
IECEx Paint Booth Explosion Proof Lighting,
ATEX Paint Booth Explosion Proof Lighting,
IECEx explosion proof spray booth lights
Tank Series Two Luminaires Assembly ATEX & IECEx Certified LED Explosion Proof Flood Light Fixtures
This user manual covers the range of ATEX and IECEx Tank Series LED normal/emergency luminaire. These luminaires are constructed with corrosion resistant epoxy coated aluminum alloy body and high impact resistance tempered glass diffuser.
Tank Series Two Luminaires Assembly LED are available from 240W to 360W, providing ideal solutions for a wide range of harsh and hazardous applications.
Features And Benefits:
1. High efficacy LED Source with long lifespan>100,000 hours.
2. 5-year performance warranty.
3. Low THD around 10%,Less interference.
4. 6KV Surge Protection.
5. Robust aluminium housing and strong tempered glass.
6. Vibration and shock resistant.
7. Low maintenance.
8. Dust proof structure design to avoid dust accumulation.
Product Important Information:
|Type Of Protection||Ex db ,Ex tb|
(IEC)EN 60079-0, (IEC)EN 60079-1, (IEC)EN 60079-28, (IEC)EN 60079-31
EN 55015, EN 61547, EN 61000-3-2, EN 61000-3-3,
EN 60598-1, EN 60598-2-5, EN 62031, EN 62493,
IEC 62321-4, IEC 62321-5, IEC 62321-6, IEC 62321-7-1, IEC 62321-7-2, IEC 62321-8
Zone 1 and Zone 2 Areas to (IEC)EN 60079-10-1,
Zone 21 and Zone 22 Areas to (IEC)EN 60079-10-2
II 2 G Ex db IIC T* Gb
II 2 D Ex tb IIIC T* Db IP66
|Temperature Class||Rated power (W)||-40℃ ≤ Ta ≤ +55℃|
|ATEx Coding||II 2 G / II 2 D|
|Ingress Protection||IP66 (IEC)EN 60529|
|Cable entry||M20*1.5,M25*1.5,3/4 NPT|
The CE marking of this product applies to EU directives 2014/35/EU, 2014/30/EU, 2012/19/EU , 2011/65/EU and 2014/34/EU respectively.
The Equipment is declared to meet the provisions of the ATEX directive(2014/34/EU)by reason of the EC
Type Examination and compliance with the Essential Health and Safety Requirements
|Voltage Range(AC)||100-277VAC (standard)|
|Standard Current Range(A)||0.57~1.6||0.72~2.0||0.86~2.4|
|Voltage Range (AC)||220~240VAC|
|Battery||9.6V 4.0Ah, Ni-MH|
1. Oil&Gas Exploration
3. Oil Reﬁnery
4. Petrochemical Plant
5. Power Plant
6. Pharmaceutical Plant
1. The first * stands for Operating Voltage including default-100 - 277 VAC , D-347-480VAC ,E-20-30VAC.
2. The second * stands for Candela Distribution including H3V3,H5V5,H6V6.
Cleaning of luminaire:
The complete luminaire (without disassemble) can be cleaned with neutral water solution. After cleaning, rinse or wipe dry with clean water.
It is forbidden to use any chemical or hydrocarbon solvent cleaner to clean the diffuser, otherwise serious damage may be caused.
Please clean the luminaire once a year if it is used under dust environment.
Disposal of Material:
Disposal of the luminaire as waste should be carried out in accordance with national regulations. Any disposal must satisfy the requirements of the WEEE directive [2012/19/EU] and therefore must not be treated as commercial waste. The unit is mainly made from incombustible materials. The control gear contains plastic, resin and electronic components. All electrical components may give off noxious fumes if incinerated.
NI-Cd batteries are defined as 'controlled waste' under the hazardous waste regulations and the person disposing needs to observe a 'duty of care'. They must be stored and transported safely and any necessary pollution control forms completed prior to transportation. Take care to fully discharge batteries before transporting, or otherwise ensure that there can be no release of stored energy in transit. For further details refer to our technical department.
Weatherproof measures should be taken during transportation.
It is strictly forbidden to load and unload violently, and it is strictly forbidden to drop and roll from high altitude, so as to prevent mechanical damage.
The luminaire should be stored in ventilated, non-dropping and non-liquid warehouse at the temperature of -20℃ to +40℃ and relative humidity ≤95%RH.
The surroundings should be kept from corrosive gases which may damage metal and insulation.
Contact Person: sales